FQLQ 450/750 V CPR
The cable may be used for fixed installation indoors and outdoors. FQLQ is suitable for installation in explosion classified areas. When installation in ground shall the cable supplies with an extra protection against mechanical stress.
StandardsNational : SS 424 02 19-4
FQLQ is a halogen free, HFFR-insulated, aluminium taped, HFFR-sheathed house wiring cable with circular, stranded copper conductors. The cable has a stranded drain wire of tinned copper under and in contact with the aluminium tape. FQLQ is designed according to SS 424 02 19-4 in applicable parts. The conductors have resistance and number of wires according to IEC 60228 class 2. The cores are identified by colours according to HD 308 (7 core cables are identidied by numbers + yellow/green). The cable has an extruded filler. The sheath is marked. type/manufacturer/year+month/metre marking. FQLQ meets the requirements for fire classification according to CPR Dcas2d2a2 . The cable emits no corrosive gases and has low smoke production during fire. The conductor insulation shall be protected against UV light that can occur for example in light fixtures and light signs. The cable is certified by Intertek.
Lifemark(TM) recycling marking
The external surface of the outer sheath is embossed with a text which specifies all components in the polymers and prepares the cable for future recycling.
Certified by Interek SEMKO.
Quality and environmental management system
Certified according to ISO 9001, IRIS, ISO/TS 16949 and ISO 14001.
|Conductor flexibility||Stranded class 2|
|Outer sheath||HFFR (polyolefin)|
|Rated Voltage Uo/U (Um)||450 / 750 V|
|Minimum installation temperature||-10°C|
|Recommended minimum installation temperature||0°C|
|Maximum operating temperature||70°C|
|Short-circuit max. conductor temperature||150°C|
|Electro magnetic interference resistance||Yes|
|Smoke density||IEC 61034|
|Gases corrosivity||IEC 60754-2|
|See all products|
Products and services
Docs and info
Declaration of Performance
Declaration of Performance No: 1000117-SEGR
- Certification Date: 26/01/2018
- AVCP (Assessment and Verification of Constancy of Performance): System 3
- Notified body : 0402
- Declared performance: Reaction to fire Dca -s2,d2,a2 according to EN50575:2014+A1:2016
|Nexans ref.||Country ref.||Product Name|
|14090198||0467605||FQLQ 450/750 V 3G1,5|
|14090298||0467625||FQLQ 450/750 V 4G1,5|
|14090398||0467655||FQLQ 450/750 V 5G1,5|
|14090498||0467685||FQLQ 450/750 V 7G1,5|
|14090598||0467615||FQLQ 450/750 V 3G2,5|
|14090698||0467635||FQLQ 450/750 V 4G2,5|
|14090798||0467665||FQLQ 450/750 V 5G2,5|
|14090898||0467695||FQLQ 450/750 V 7G2,5|
|14090899||0467694||FQLQ 450/750 V 7G2,5|