AXQJ TT 12 kV 1-core
The cable has a circular aluminium conductor, XLPE-insulation, copperscreen, AL/PE-tape and HFFR-sheath.
StandardsInternational : HD 620.10K
National : SS 424 14 16
- Conductor Circular, stranded aluminium conductor with resistance and number of wires according to SS 424 14 08. The conductor is longitudinally water blocked according to SS 424 14 17.
- Inner conducting layer Semiconducting crosslinked polyeten.
- Insulation Crosslinked dry cured polyeten (PEX).
- Outer conducting layer Crosslinked strippable conducting elastomer.
- Screen One layer of circular annealed copper wires, locked with swelltape.
- Moisturebarrier sheath Alongrunning plasticcoated aluminiumtape applied with glued overlap. The tape adheres the outher sheath.
- Sheath Black HFFR polyolefin. The sheath is marked, ie: "NEXANS GS AXQJ TT 12 kV 1 x 240/35 Ds2d2a2 year month" + metremarking.
The following applies if presstools are used:
The actual copperscreen are one cross section lower than the typemarking. This means that if the screen is 25 mm² the connector should be 16 mm².Al tape is grounded to the copper wires and don´t need to be connected in joints or terminations.
Lifemark(TM) recycling marking
The external surface of the outer sheath is embossed with a text which specifies all components in the polymers and prepares the cable for future recycling.
The cable is in appliable parts constructed according to HD 620.5-K. The cable can be loaded according to SS 424 14 16.
Quality and environmental management system
Certified according to ISO 9001, IRIS, ISO/TS 16949 and ISO 14001.
|Conductor shape||Round, stranded|
|Outer sheath||HFFR (Halogene Free Flame Retardant)|
|Number of cores||1|
|Minimum installation temperature||-10°C|
|Recommended minimum installation temperature||0°C|
|Maximum operating temperature||90°C|
|Short-circuit max. conductor temperature||250°C|
|Water proof||Longitudinal & radial|
|See all products|
Products and services
Docs and info
Declaration of Performance
Declaration of Performance No: 1000537-SEGR
- Certification Date: 17/08/2017
- AVCP (Assessment and Verification of Constancy of Performance): System 3
- Notified body : 0366
- Declared performance: Reaction to fire Dca -s2,d2,a2 according to EN50575:2014+A1:2016
|Nexans ref.||Country ref.||Product Name|
|21191198-201-05||0088065||AXQJ TT 12 kV 1x95/25|
|21191398-201-05||0088085||AXQJ TT 12 kV 1x240/35|
|21191698-201-05||0088105||AXQJ TT 12 kV 1x630/35|