MQQ 750 V (feeder cable)
The cable may be used for permanent installation on ladders, directly in walls, concrete, in conduits or ducts. The cable has a small outer diameter and can be pulled i.e. existing pipes as feeder cable to apartments in renovation project. For use indoors and outdoors but not in ground or water. The cable have protection against exposure of UV-light.
StandardsNational : SS 424 02 19-5
MQQ is a halogen free, HFFR-insulated and HFFR-sheathed house wiring cable with circular, stranded copper conductors. The cable is designed according to SS 424 02 19-5. The conductors have resistance according toIEC 60228 class 2. There are more number of wires in the conductor than the requirements in IEC 60228 class 2, for an easier handling. The cores are identified by colours according to HD 308. The sheath is marked. type/manufacturer/year+month/metre marking. MQQ meets the requirements for flammability class Dcas2d2a2 according to CPR and have protection against exposure of UV-light according to HD 626 S1 part 2.5.1. The conductor insulation shall be protected against UV light that can occur for example in light fixtures and light signs. The cable is certified by Intertek SEMKO.
Lifemark(TM) recycling marking
The external surface of the outer sheath is embossed with a text which specifies all components in the polymers and prepares the cable for future recycling.
Certifeid by Intertek SEMKO.
Quality and environmental management system
Certified according to ISO 9001, IRIS, ISO/TS 16949 and ISO 14001.
|Conductor flexibility||Stranded class 2|
|Outer sheath||HFFR (polyolefin)|
|Nominal outer diameter||13.2mm|
|Rated Voltage Uo/U (Um)||450 / 750 V|
|Minimum installation temperature||-10°C|
|Recommended minimum installation temperature||0°C|
|Maximum operating temperature||70°C|
|Short-circuit max. conductor temperature||150°C|
|Smoke density||IEC 61034|
|Gases corrosivity||IEC 60754-2|
|Bending factor when installed||6(xD)|
|See all products|
Products and services
Docs and info
Declaration of Performance
Declaration of Performance No: 1000640-SEGR
- Certification Date: 12/01/2018
- AVCP (Assessment and Verification of Constancy of Performance): System 3
- Notified body : 0366
- Declared performance: Reaction to fire Dca -s2,d2,a2 according to EN50575:2014+A1:2016
|Nexans ref.||Country ref.||Product Name|
|14141098-412-05||0455405||MQQ 450/750 V 5G4 stigarkabel|