MILLICABLE/2 400/6 (HS)
Country ref. 8935166
StandardsInternational : IEC 60332-1; IEC 60335-2-96; IEC 60800
Declaration of Performance : Reaction to fire: Eca
according to EN50575:2014+A1:2016
Thin twin conductor heating cable units for both renovation and new buildings. The units can be installed in two different ways:
1. MILLICABLE™ in combination with MILLICLICK™ boards. MILLICABLE™ can be installed directly under wooden floor coverings like parquet, laminate etc. without any use of concrete or levelling compound. The MILLICLICK™ boards have pre-cut slots for the cable, which makes the installation very easy to perform. The boards are placed on a stable and levelled subfloor. By using MILLICLICK™ boards, the area power will be 60 W/m². Install standard parquet underlay between the parquet and the MILLICLICK™ boards.
2. MILLICABLE™ installed as a conventional heating cable. MILLICABLE™ is installed as a freely laid cable and attached to the subfloor in the planned C-C distance. The heating cable is then covered with screed or concrete, minimum thickness 5 mm, where the entire cable must be covered.
Minimum installation temperature (without any precautions) 0 °C.
|Number of conductors||2|
|Type of conductor||Solid, Class 1|
|Drain wire||Solid tinned copper|
|Type of splice||Intergrated/hidden|
|Maximum outer diameter||4.2mm|
|Approximate net weight||2.3kg|
|Nominal element resistance||131.5Ohm|
|Max. element resistance||144.6Ohm|
|Min. element resistance||124.9Ohm|
|Length of cold lead||3.5m|
|Flame retardant||IEC 60332-1|